It is manufactured from High conductive shaped Aluminium conforming to IS:8130-1984, which provides maximum conductivity to the flow of electricity thus, helping to save the energy.
Conventional Poly Vinyl Chloride (PVC) insulation of Type-A conforming to IS:5831-1984
The separate insulated two cores are laid side by side to form flat shape so these cables envisage the requirement of sheathing AMBY VELLY Cables provide exclusively formulate PVC compound for sheathing to meet all the National Standards to minimize the electrostatic and mechanical breakdown.
|Area of Conductor
|No./Dia of each strand (mm)||Nom. Insulation Thickness
|Nom. Sheath Thickness
|Overall Diameter Max.
(B x W)
|Resistance at 20⁰ C
|2.5||1/1.78||0.7||1.0||10.5 x 6.6||12.1||18|
|4.0||1/2.25||0.8||1.0||12.0 x 7.4||7.41||23|
|6.0||1/2.76||0.8||1.1||13.0 x 8.0||4.61||30|
|10.0||1/3.57||1.0||1.4||16.0 x 9.6||3.08||40|
|16.0||7/1.70||1.0||1.4||18.5 x 11.0||1.91||51|
|25.0||7/2.132||1.2||2.0||22.5 x 13.0||1.20||70|